Fire performance data
To ensure the Automist® product range is fit for purpose, Plumis carried out fire testing at Maryland Fire and Rescue Institute, the Exova Warrington UKAS Laboratory (UK) and the Building Research Establishment (UK) including everything from standardized sprinkler tests to real life scenarios.
Automist Smartscan® has been tested in-house against all relevant UL 2167 (Standard for Water Mist Nozzles for Fire Protection Service) clauses in preparation for listing. In addition, Automist Smartscan® has met the fire performance standards outlined in BS 9252:2011 (Components for residential sprinkler systems. Specification and test methods for residential sprinklers) and BS 8458:2015 (Fixed fire protection systems. Residential and domestic watermist systems. Code of practice for design and installation), and is covered by a UK LABC Registered Detail (EW534). Automist has also been tested in a range of realistic fire scenarios like oil pan fires, obstructions and shielding, to assess its fire fighting performance.
Free Technical Information Pack
Download our Technical Pack which contains information detailing how Automist® uses a high-pressure pump to provide whole-room watermist fire protection. It shows how Automist® can be retrofitted without major disruption. Provides links to download third party reports of the extensive testing conducted by Exova Warringtonfire. Automist Smartscan® has met the fire performance standards outlined in BS 9252 and BS 8458, the UK equivalent to UL 2167.
The Automist® sprinkler alternative technical Information pack includes:
Independent 3rd party test reports from the Exova Warrington UKAS Laboratory.pdf
Declaration of testing and conformity.pdf
A fire suppression device like Automist ® aims to control and suppress fires, significantly reducing the risk of injury, life loss and property damage by maintaining tenable conditions for as long as possible while occupants evacuate. This is achieved in several ways:
Reduction of room temperature in the region of the fire. Water mist devices achieve this by consuming much of the fire’s energy in converting water to steam.
Reduction of smoke and toxic gases. Water mist devices achieve this by the production of copious amounts of inert steam in the immediate vicinity of the fire, locally excluding oxygen, reducing temperatures and thus slowing the oxidation reactions of the fire.
Flashover prevention. By constraining room temperatures to around 212°F or less, flashover (the rapid ignition of combustible items in the room) is prevented.
Providing cooling to structural elements of the home that are in the spray path, allowing them to resist the fire for longer.